As per the demands of the industry and of our clients, we offer large range of Industrial RO Systems such as 100lph,150lph,250lph,500lph 1000lph,2000lph ro plant,4000lph ro plant etc that are used in various industries to improve the color, taste and other properties of drinking water. In order to meet the international quality standards, these are manufactured using qualitative raw material and latest technology.valued customers can avail the range of highly reliable Industrial RO Systems. Industrial RO Plant 2000LPH that are developed as per international quality norms and client’s technical demands. Widely appreciated for optimum performance, high water carrying capacity and low maintenance, our range of Industrial RO Systems 2000 LPH are highly demanded across various industries. Offered at industry leading rates our range has been successful in meeting clients’ demands and satisfy their water purification needs.
- Production Capacity: 2000 LPH
- Filter Cartridge: 1 No 20’ each
- Inlet Water Pressure: 7 Kg to 14 Kg
- Booster Pump: Multi Stage.
I.> Basis of Design (2000lph ro plant)
2000lph ro plant, Industrial MODEL : (DLX-R2000)
A. Limiting parameters of R O feed water
Total Hardness (As CaCO3) Total Dissolved Solids Turbidity Silt Density Index Free Chlorine / Strong oxidizing agent Nil
Oil & Grease Nil
Iron Fluoride Heavy Metal Nil
Temperature 250 C
Note: All limiting conditions herein must be observed during the plant operation for satisfactory performance throughout the plant life.
B. Parameter Flow Rate
Impurities Filter Ratio 95% of raw water (I.e. 100ppm of 2000ppm)
Recovery Ratio 40% : 60%
Flow Rate 2000 Liters Per Hours
II. > Equipment wise specifications< 1- Raw Water Pump used in 2000 lph ro plant: Purpose: To feed the dual media filter at pressure more than 2.0 bars, which is min. operating pressure for filters. Sl. Parameter Qty. Description (a) MOC 01 set Cast Iron (b) Type Horizontal Centrifugal © Flow Rate 3800 Liters per hour (d) Head 35m © Power Required 1.6 KW (f) Electrical 440V, 50HZ (g) Cycle 2900 rpm (h) Make CRI (i) Model KDS225+ 2. Multi Grade Sand Filter: Purpose: To remove the suspended solids, dirt, iron, and reduce silt density Index, which can foul the membranes. Sl. Parameter Qty DESCRIPTION (a) Make 01 Set Pentair Water, USA (b) MOC FRP (Fiber Reinforcement Plastic) © Diameter 780mm x 1829mm (d) Volume 710 Liters (e) Working Pressure 3.5 Kg/cm2 (f) Media Anthracite, pebble and fine sand (g) Qty. Media Filling 550 Five Hundred Fifty Kilogram (h) Operating Valve Multiport Valve (Midas from Germany) 3. Activated Carbon Filter: Purpose: D-chlorinate and oxidize raw water to feed RO membranes. Sl. Parameter Qty DESCRIPTION (a) Make 01 Set Pentair Water, USA (b) MOC FRP (Fiber Reinforce Plastic) © Diameter 780mm x 1829mm (d) Working Pressure 3.5 Kg/cm2 (e) Media Activated Carbon 1000IDV (f) Qty. Carbon Filling 450 Four Hundred Fifty Kilogram (g) Operating Valve Multiport Valve (Midas from Germany) 4. Piping and Fittings: Internal Piping of Stainless steel 304 and U-PVC tested pressure 25 Bar. Specifications: High class tubing for long life on highly brackish water. Sl. Parameter Qty. DESCRIPTION (a) Make 01 Lot U-PVC (b) MOC U-PVC Astral (c ) Burst Pressure 25Kg/Bar (d) Size 40mm 5. Anti-scaling Dosing System: Purpose: To prevent scale formation on RO Membranes. Specifications: Electricity operated dosing pump with PVC 100 Liters Sl. Parameter Qty DESCRIPTION (a) MOC PP (b) Capacity 6 LPH (C ) Pressure 5 bar (d) Qty. 1 nos. One nos. (e) Make e-Dose 6. Micron Filters: Purpose: To remove suspended solids and turbidity by filter fine particles up to .01 microns. Housing: Sl. Parameter Qty. DESCRIPTION (a) Make 02 set RAVE Filtration (b) MOC of Housing Mild blow Poly Propylene (c) Length 20” (d) Diameter 5.5” Cartridge (f) Make Pure & Safe (g) Cartridge MOC Polypropylene Big Blue Cartridge (h) Length 20” (i) Diameter 4” (k) Micron Rating 05 Micron + 10 Micron 7. High Pressure Pump used in 2000lph ro plant: Purpose: To feed the RO membranes at adequate pressure for filtration process take place. Specifications: Multistage Vertical Stainless Steel pump Sl. Parameter Qty. DESCRIPTION (a) MOC SS 316 (b) Type Centrifugal Pump (c) Flow Rate 3800 Liters Per Hours (d) Head 160mwc (e) Power Required 3.2 KW, 440V (f) Model 2-22 (g) Cycle 2900 RPM (h) Make CRI (i) Quantity 1 set One set 8. RO Pressure Vessel: Purpose: To pack Reverse Osmosis Membranes and operate at high pressure up to300 psi. Specifications: Sl. Parameter Qty. DESCRIPTION (a) MOC FRP in Code Line (b) Diameter of pressure Vessel 8.5 Inch (c) Length of Pressure vessel 40 inch (d) No. of Pressure vessel 2 set Single barrel for one element (e) No. of Membranes in vessel 1 Nos. (f) Make Pentair Water from USA (g) Position Horizontal in Series (h) Pressure Rating 300psi 9. RO Membrane in 2000lph ro plant: Purpose: To remove the major part of TDS up to 98% by Reverse Osmosis Membranes arranged and designed to give adequate flow and recovery. Specifications: Thin film composite membrane based on filtration .0001Micron Sl. Parameter Qty DESCRIPTION (a) Type/Model Spiral Wounded, BW8040 (b) Diameter of Membrane 8.0 Inch (c) Length of Membrane 40” Inch (d) No. of RO Membranes 2 Nos. Two Nos. (e) Recovery per Membrane 15-20% (f) Salt rejection per Membrane 98-99% (g) Make of Membrane CSM (h) System Recovery 35% 10. Electrical Panel Purpose: MMIC Controller is provided as a safety measure for the pumps & electrical items. Specifications: For automatic operation like switch on and off and help to active all sensors. Sl. DESCRIPTIONS (a) Complete Starters, overload relays. (b) Voltmeter, Ammeter, MCB’s Indicating Lights (c) Push Buttons (d) Rocker switches for dozers (e) Incomers Auto-manual switches (f) Auto+ Manual operation in case of emergency 11. Instrumentation Sl. Equipments Specifications (a) Flow Meter To measure the online flow of water (b) Low Pressure switch To protect RO pump from dry Running (c) High Pressure Switch To Protect RO pump from back pressure (d) Pressure Gauges For calculate ^ P for each unit in RO system Specifications: (a) Rota Meter Particulars Qty. Description Uses 3 nos. Permeate, Reject & Raw Range 1.0 cu. m. per hour Make LINQ/Flow max (b) Pressure Switch Particulars Qty. Description Quantity 2 nos. Low + High, Switch for Industrial application Range 30-500 psi Make Indofoss (c)Pressure Gauges Particulars Qty. Description Quantity 5 nos. On various pressure point Range 0-21 Bar Dial Size 4 inches Type Bourdon Make H-Guru MOC SS 316